Home Improvement & Tools, Measurement and Analysis | Digital Voltmeter | Measuring Tools, Tools
XH-W3001 W3002 12V 24V 220V LED Digital Control Thermostat Temperature Microcomputer Switch Thermometer Thermoregulator Sensor
$22.29 – $28.65
Both W3001 and W3002 are direct output types.
The W3001 can only set the start and stop temperatures.
The W3002 has more temperature correction and delay start than the W3001.
AC-DC converters make your products safer.
XH-W3001 W3002 12V 24V 220V LED Digital Control Temperature Microcomputer Thermostat Switch Thermometer Thermoregulator Sensor
Size(Length x Width x Height): about 5.5 x 3.8 x 3.2cm (2.17 x 1.50 x 1.26rdquo )
Supply Voltage: DC 12V / 24V / AC 90~250V
Temperature Measurement range: -50-110℃
Temperature Control Range: -50-110℃
Control Accuracy: 0.1℃
Display Accuracy: 0.1℃
Measuring Input: NTC10K Waterproof Probe L=1 Meter
Output Type: Relay Output(Output Switch)
Output Capacity: 10A
Introduction to code and features
PO setting start temperature
Press the Setup button to enter the internal menu. The default display is PO. Press the Setup button again to set the required startup temperature with the up and down buttons.
P1 sets the stop temperature
Press the setup button to enter the internal menu, the display is P0, switch to P1 by the up and down keys, press the setup button again, and set the required stop temperature by the up and down buttons.
P2 set temperature correction
In the same way, enter the internal menu, switch to P2 by pressing the up and down buttons, press the setting button again, and set the required calibration temperature by the up and down buttons. (Note: In the setting, if the detected temperature value is 0.5c larger than the actual temperature value, then the calibration temperature to be set is -0.5'C. If the detected value is 1'C smaller than the actual temperature value, the calibration temperature to be set is 1 'C, detection temperature + corrected temperature = actual temperature.)
P3 set delay start
In the same way, enter the internal menu, switch to P3 by pressing the up and down buttons, press the setting button again, and set the required delay time by the up and down buttons, the unit is minute. (Note: Delay start is generally used for compressor refrigeration. If it is used in refrigerator freezer, this value needs to be set. According to compressor back pressure, the general setting is 3-6 points, if you are not using it for control or No delay function is required, skip it directly.
Note: The appearance of the product may vary somewhat depending on the production lot. But the performance is the same.